Automatic B-stream setting
To separate the front hall from the cold store, three air streams are utilised, all of which have the same direction and speed, but differ in temperature and air humidity. These air streams work by intaking air from both the cold store and front hall, and then discharging cold and warm air in the doorway. However, the two outer air streams have a significant difference in temperature and absolute air humidity which can lead to condensation where the streams meet. To prevent this, an intermediate air stream (B-stream) is introduced, which is drawn from the cold store and heated, resulting in relatively low humidity. By adding this intermediate air stream, condensation is avoided, and the separation of the front hall from the cold store is maintained effectively.
Stable climate in the refrigerated warehouse
Always on the correct setting (automatic B-stream regulation)
No mist and no ice buildup
Enhance your customers' shopping experience and save on energy costs with Biddle's innovative climate solutions.